Power Plant Labelling Sytem (KKS Numbering Code) Checklist for Civil Procedure. a helpful checklist when running through a civil procedure exam. Mar 8, MEDUPI POWER STATION I Doc No-: KKS01 I Rev: 1 KKS CODING AND LABELLING Doc Type: Procedure Page 2 of 26 Contents 1. Purpose. Procedure for Plant Identification(KKS Numbering System). Uploaded by Tung Hoang Power Plant Labelling Sytem (KKS Numbering Code). Uploaded by.
|Published (Last):||22 December 2008|
|PDF File Size:||16.60 Mb|
|ePub File Size:||12.67 Mb|
|Price:||Free* [*Free Regsitration Required]|
Identification System for Power Stations (KKS)
CF means the twelfth local measuring circuit of fluid flow the code CF12 is not correct. The first digit is often used to point the kind sort of component designated in B1 B2. The identification letters now used twging the Point of installation identification in the breakdown level FUNCTION are the same as those for the process-related identification.
If this is not the case, txging floor numbering codes of the total plant must be written uniformly with three data characters in AN. Inosanto Numbering System Inosanto Kali notes. Coding letters and designations of main groups B1 for components as given in the Component Key and for signals and signal applications: X Signal origins Y Signal applications Z Gated signals No generally valid rules have been made for signal procesure application areas.
Total plant Serial no. Installation Unit Code Serial no. We share information about your activities on the site with our partners and Google partners: The following example illustrates the structure of the Point of Installation Code: Tooth Numbering System Word File tooth no. The grid sizes and the meaning and type of the data characters A or N are subject to agreement between the parties to the project.
The Equipment Unit identified in breakdown level 2 belongs always to the System designated in breakdown level 1. Z — Workshop and office equipment The additional code can be omitted. They are generally identified after the system within the interfaces of which the sensor is installed. YB81 XB82 Auto; close, down F Point of Installation Identification This designation is used for the proceddure of installation identification in assembly units for instrumentation and control system for e.
Feed water system Control and protection system for steam, LY. Point of Installation Identification For this purpose, data character B1 can contain: Gated analog signals tabing physically similar direct measured variables are identified by means of kka set number, e.
KKS Identification System for Power Plants – Function and Type
Details of application are subject to agreement between the parties to the project. System numbering must consist of two digits. Generally valid rules on the use of FN numbering are not expedient.
Exceptions are junction boxes for main machine sets and heavy machinery, and junction boxes in electrical and control and instrumentation cubicles and cabinets; these are identified on breakdown level 1 according to the associated main machine or heavy machine and cubicle or cabinet respectively. Remember me on this computer.
Order according to voltage levels, counted from higher voltages to lower. System code System code consists of three letters and two digits. The numerical digits count and subdivide the unit e. Types of Code and Breakdown Levels Special Rules for Civil Engineering This code unit can be combined with any breakdown level as necessary for identification.
Room Identification by Coordinates Serial no. In the electrical and instrumentation control engineering sectors, the equipment for auxiliary services, power supply, open-loop-control, instrumentation, etc.
Procedure for Plant Identification(KKS Numbering System)
Steam, water, gas cycles Q. Valves Valves are identified on the equipment unit level by the letters AA regardless of their type, design or actuator. Requirements to be met by the Identification System To perform the set tasks the Identification system must be capable of satisfying the following requirements: No one of these symbols can be omitted.
This improves recognition of the identification in the overall system. They are made up of classifying and numbering code elements. Steam, water, gas cycles CJA common to H. Enter the taginh address you signed up with and we’ll email you a reset link. Calculation of new value on base of 2 variables, e. B — Mechanical equipment Examples Examples of the identification of installation spaces in panels To identify the installation space, draw on front of the panel coordinate system origin – so called grid.
EB – Conditioning of signals related to single drive control. B — Power transmission and auxiliarY electrical power supply Equipment Unit-Specific Analog Signal Processing and Measuring Circuits Equipment unit-specific analog signal processing elements comprise control and instrumentation equipment which is only provided for one equipment unit such as tagin interface, protective logics, instruments in the feeder and command termination for final control elements.
Because relevant design progress have been done too much. EY – Conditioning of signals related to functional protection group of technical and electrical protection system of the unit. The origin and development of KKS YB71 XB72 Control room; close, down F Equipment Unit Key, groups A1: Checklist for Civil Procedure a helpful checklist when running through a civil procedure exam.
Control and Instrumentation Equipment